Add: Industrial Concentration Zone(North) Of Wanshi Town, Yixing District, Wuxi, Jiangsu Province, China
During operation, the cooling medium is driven by a main circulating pump circulating flow between the heat exchanger and the equipment. The water is sprayed on the heat exchanger to uniformly form a water film on the heat exchange surface. Cold air enters the tower from the underlying air inlet through the surface of the heat exchanger surface....Send Inquiry Chat Now
Structure and working principle
During operation, the cooling medium is driven by a main circulating pump circulating flow between the heat exchanger and the equipment. The water is sprayed on the heat exchanger to uniformly form a water film on the heat exchange surface. Cold air enters the tower from the underlying air inlet through the surface of the heat exchanger surface. There are two methods of heat exchange in this process. Heat transfer between the cold air and the cooling medium, as well as the heat exchange of the steam and the heat absorption of the water spray. Hot air is vented from the air to the atmosphere. Other water flows into the sink below the tower. Then pump them into the sprinkler system. The cooling medium in the reciprocating heat exchanger is cooled.
1. Adopt the inverter argon arc welding process and pass the 2.75mpa pressure test for many times to ensure the welding quality and overall pressure resistance.
2. The alloy galvanized steel sheet of the shell has good moisture resistance, oxidation resistance and corrosion resistance.
3. Cooling tower special motor, fan and unique drenching and elimination technology are adopted
1. Before you choose the product, you can provide us with the inlet water temperature, the outlet water temperature, and the air wet bulb temperature.
2. Our products can run at -50 ° C, the coldest average temperature is below -10 ° C, you should tell us when ordering, we will take anti-ice measures.
3. Circulating water turbidity is less than 50 mg / L, free of oil and impurities.
4. The inlet water temperature is below 60 °C.
5. The inlet and outlet pipes can be rotated by 90°, 180° and 270°.
6. The fan blade angle is adjustable to ensure the same angle.
7. Do not exceed the rated current of the motor.
8. Pay attention to fire and pressure.
(1) Tell customers how to use our products
(2) Guide customers to choose the best and economic product, recover the investment within short time. In-Sale services:
Quality control must be inspected strictly.
Usually, our product warranty is 18 months after leaving factory or 12 months after installation. within this months, all parts broken will be responsible for our factory.
(3) Regular contact with customers. Update our products based on the feedback of customers.