Add: Industrial Concentration Zone(North) Of Wanshi Town, Yixing District, Wuxi, Jiangsu Province, China
Evaporative condensers mainly use the evaporation heat of water to remove the condensation heat of the refrigerant. 1 liter of water evaporation can take away 670W of heat. The water-cooled condenser uses the temperature of the water to absorb the heat, and 1 liter of water only takes away 5W~6W of heat. The effluent of the evaporative cold configuration has high dehydration ability, and the water loss loss is small, and it can be used safely in areas with drought and low water.
1. The condensation temperature is low, and the summer high pressure is not high.
2. Air-cooled water-cooled combination, water-saving, electricity
3. Easy to install and easy to use
4. Aluminum-zinc casing is durable
6.Simple structure, easy to remove scale, small size
The evaporative condenser can be placed directly on the top of the machine room. There should be no buildings around the air that will affect the flow of air. Otherwise, it will cause hot air to flow back, increase the wet bulb temperature of the fresh air at the air inlet, and have a certain impact on the condensation effect. . If the surrounding environment cannot be avoided, an exhaust duct can be installed at the hot air outlet to increase the discharge height, which should be equal to the height of the surrounding buildings. When evaporating the condenser, be sure to pay attention to the pressure balance problem with other equipment. Since the condensing pressure of the evaporative condenser is affected by various factors such as ambient temperature, fan air volume, circulating water volume, and air in the coil, safety valves must be installed on the inlet and outlet sections of the cooling coil for safe use.